消防信号闸阀是在特制手动暗杆闸阀的基础上加设电信号装置而成。阀门除了按国家标准设计制造外，并按此阀在自动喷水灭火器系统安装及使用特点，采用不锈钢精磨阀杆及便于维护的四氟 U 型密封，并增设了独特的 O 型圈阀杆上密封（导密封）结构，能够确保阀门长期处于常开状态下，阀杆不渗漏，有利于吊顶中安装使用。
The fire signal gate valve is made by adding an electrical signal device on the basis of a special manual Non rising stem gate valve. In addition to the design and manufacture of the valve according to the national standards, and according to the installation and use characteristics of the valve in the automatic sprinkler system, the stainless steel fine grinding valve rod and the tetrafluoro U-shaped seal for easy maintenance are adopted, and the unique O-ring upper seal (guide seal) structure of the valve rod is added, which can ensure that the valve rod does not leak when the valve is normally open for a long time, which is conducive to installation and use in the ceiling.
The electrical signal device is a fully sealed precision electromechanical box structure. The box adopts stainless steel parts and imported electrical components. The device is arranged on the valve body gland which is not easy to be collided under the operating handwheel. It is equipped with micro motion shape and pushing mechanism to connect the gear with the "on" and "off" electrical signals fixed at the opening and closing position of the gate valve.